Good news, all of the roof work has been approved by the city and we now have a permit for everything. Also, we're already in the process of getting some of the various inspections done, etc. so we should be able to get an occupancy permit very shortly after everything is completed.
Plumbing: New bldg domestic water riser coring in-progress from Basement to 8th Floor. Piping install in-progress in basement.
Dock: Temporary tap gen box installed.
Vertical Risers: Hogan ground boxes installed.
A/C condenser relocation: Condenser lines removed from future ComEd Vault.
Basement Construction Progress Summary:
Existing Electrical Room: Ground to water service in-progress.
Boiler Room: Building stored items primarily removed.
Future Elec Room: Hogan Ground box installation in-progress
6th Floor Construction Progress Summary:
Doors/Windows: Awaiting man doors.
Finishes: Awaiting primer and finish paint.
Floors: Conc housekeeping pads expansion complete.
Electrical: UPS Parallel board installed and conduit installation in-progress as well as lighting.
Mechanical (Chilled water): Chiller lines complete, awaiting CRAH 5 and insulation.
Mechanical (Vent): Room exhaust vents and supply vent near complete
7th Floor Construction Progress Summary:
Tennant: Moved misc. equipment into 7th floor storage area.
Doors: Complete except card readers and elec. strikes.
Floors: Complete. Tile trim req. at suite door.
Voice/Data Security: Card reader and elec. strikes req.
Mechanical (Chilled water): Completed through HVAC closet, awaiting insulation.
8th Floor Construction Progress Summary:
Walls: Room walls complete.
Doors/Windows: Awaiting door install.
Floors: Handrails @ stairs and ramp complete. Toilet access floor complete.
Ceilings: Ceiling tile installation in-progress in Office and toilets
Voice/Data Security: Wire cable tray install in-progress in Data Center, Security cable pull in-progress.
Electrical: PDU grounding near complete, exit signs complete, wiring for fire alarm @ the total pac and smoke detection near complete.
Plumbing: Awaiting fixtures
Fire Alarm: Fire alarm control panel installed, wiring in-progress.
Mechanical (Chilled water): Variable frequency drives, Chemical Pot Feeder and filter installed and piping near complete.
Mechanical (Vent): Drips pans complete, ductwork near complete.
Sprinklers: Total Pac piping complete, sprinkler heads complete.
Finishes: Primer and first coat paint complete.
Freight Elevator: Elevator cab, frame and curb raised and back in-service.
Miscellaneous: Window screens replaced
Roof Construction Progress Summary:
Exterior: Curbs for AHU-A and CU1 & CU2 complete.
Interior: Elec room door completed.
Elec: Ground box installed.
The pictures: http://steadfast.net/images/march31progress.pdf