I'm caught up again with the reports and I have some good news and I have some bad news. Good news is that everything inside is progressing nicely and nearing completion. The data center floor itself is basically done, CRAC units installed, busway is fully installed, PDUs are connected up, etc. but the bad news is there have been some delays in other aspects. The UPS unit/configuration had some issues with availability delivery and are a couple weeks behind. In addition, there has been further issue with permits for the structural steel, generator, and chiller configuration for the roof, which is also a delay of several weeks. Right now, it is looking like we'd be opening closer to June 1.
Dock: Temporary tap gen box installed.
Vertical Risers: Hogan ground boxes installed.
A/C condenser relocation: Condenser lines removed from future ComEd Vault.
Basement Construction Progress Summary:
Existing Electrical Room: Ground to water service in-progress.
Boiler Room: Building stored items primarily removed.
Future Elec Room: Hogan Ground box installation in-progress
6th Floor Construction Progress Summary:
Doors/Windows: Exterior windows tinted, awaiting man doors
Walls: Primarily complete
Finishes: Awaiting primer and finish paint
Floors: Conc housekeeping pads complete
Mechanical (Chilled water): Chiller lines complete, awaiting CRAH 5 and
7th Floor Construction Progress Summary:
Tennant: Moved misc. equipment into 7th floor storage area.
Doors: Complete except card readers and elec. strikes.
Floors: Complete. Tile trim req. at suite door.
Voice/Data Security: Card reader and elec. strikes req.
Mechanical (Chilled water): Completed through HVAC closet, awaiting insulation
8th Floor Construction Progress Summary:
Walls: Toilet build-out from deck to clg and lower floor.
Doors/Windows: Rear window used for CRAH walled up.
Floors: Awaiting handrails.
Ceilings: IDF Ceiling and soffit near complete, elevator lobby complete.
Voice/Data Security: Installation of blue color pipe for Steadfast security and
yellow for data in-progress.
Electrical: Install of lights and motion detectors, Starline Power rails installed and wire pulling to PDU’s in-progress.
Plumbing: Drain pan installed under overhead lines.
Fire Alarm: Fire alarm control panel installed.
Mechanical (Chilled water): Connections to CRAH units in-progress, insulation
Mechanical (Vent): Roof equipment arrived and installation in-progress including AHU-A, Condensers, exhaust vents. Ceiling supply and diffusers installation in-progress.
Sprinklers: Total Pac piping in-progress, sprinkler heads being set, heat
Finishes: Primer and first coat paint complete.
Freight Elevator: Elevator cab, frame and curb raised and back in-service.
Roof Construction Progress Summary:
Exterior: Exhaust fan installation in-progress.
Interior: Elec room door completed.
Elec: Ground box installed.