With more finish work getting done in the office areas and the floors being finished in the data center space things are starting to look more complete, though there is still a lot to go. Once the raised flooring gets put in though, things will start looking more like a real data center.
Here is the status update as of Dec. 16:
Basement Construction Progress Summary:
Existing Electrical Room: Concrete transformer housekeeping pad complete. Temp transformer on-site awaiting installation. Conductors pulled from new CT cabinet to exist switch board and transformer location.
7th Floor Construction Progress Summary:
Walls: Modifications complete awaiting paint.
Doors: Doors & frames installed except double door and suite entry door.
Floors: Floor prep complete. VCT tile installation in-progress.
Ceilings: New lighting and ceiling tile installed.
8th Floor Construction Progress Summary:
Walls: Partition framing complete – gypsum board not installed
Floors: Latex coat over carpet glue complete and sealed.
Ceilings: Painting complete.
Electrical: Roughing in-progress for switching, lights, voice/data and security.
Plumbing: Existing plumbing removed. Minor plumbing work started.
Then here are the pictures: http://steadfast.net/images/dec16progress.pdf